The motors control center of the BTM group has a modern, strong, flexible construction and has the easiest operational system in the market. Its project was totally developed using the Pro/Engineer 4.0. tool.
Evidence of the excellent quality of its components and its construction, the MCC was tested in the NBR - IEC 60439-1 norm “Sets with tests from completely tested types, and approved by the competent organs such as, CEPEL, IEE and IPT of Universidade de São Paulo.
We develop customized projects
Strict quality control NBR ISO 9001:2000
Meets the regulation NR10
Meets the regulation NBR 5410
Meets the regulation NBR - IEC 60439-1
Construction: Form 1, 2A, 2B, 3A, 3B, 4A e 4B (NBR - IEC 60439-1). Structure in plate #12 MSG, outer covering in plate #14 MSG,
supports in plate #14 MSG (Galvanized).
Dimensions: Width 800mm. | Height 2200mm + 100mm (Rodapé). | Depth 800 mm (for other dimensions, contact us).
Protection Level: IP-40 to IP-54.
Nominal Voltage: 660V (for other voltage, contact us).
Nominal Electric current: up to 3150A (for other electric currents, contact us).
Symmetrical short-circuit electric current: 65kA (for other electric currents, contact us).
Test Voltage of industrial frequency: 2500V.
External finishing: Munsell N6.5 - 80 microns | Internal/ External Use - 140 microns (for other colors, contact us).
Desenvolvimento de CCM em 3D
Foto Vista Frontal de CCM Baixa Tensão